Theoretical and experimental investigations of the flow and temperature distribution in a $12.53m2$ solar collector panel with an absorber consisting of two vertical manifolds interconnected by 16 parallel horizontal fins have been carried out. The investigations are focused on overheating and boiling problems in the collector panel. Single-phase liquid flow and heat transfer in the collector panel are studied by means of computational fluid dynamics (CFD) calculations. Differently designed collectors are investigated with different collector fluid volume flow rates. The effect of friction and the influence of the buoyancy effects are considered in the investigations. Further, experimental investigations of the solar collector panel are carried out. The flow distribution through the absorber is evaluated by means of temperature measurements on the back of the absorber tubes. The measured temperatures are compared to the temperatures determined by the CFD model and there is a good agreement between the measured and calculated temperatures. Calculations with the CFD model elucidate the flow and temperature distribution in the collector. The influences of collector fluid flow rate and inlet temperature on the flow and temperature distribution are shown. The flow distribution through the absorber tubes is uniform if a high flow rate of $10.0l∕min$ is used. By decreased collector fluid flow rate and by increased collector fluid inlet temperature, the flow distribution gets less uniform due to the influence of buoyancy force. If the collector fluid flow rate is small and the collector fluid inlet temperature is high enough, severe nonuniform flow distribution may happen with a small flow rate or even zero or reverse flow in the upper horizontal strips, resulting in overheating or boiling problems in the strips. The CFD calculations elucidate the flow and temperature distribution in the collector panels of different designs. Based on the investigations, recommendations are given in order to avoid overheating or boiling problems in the solar collector panel.

1.
Duffie
,
J. A.
, and
Beckman
,
W. A.
, 1991,
Solar Engineering of Thermal Processes
,
2nd ed.
,
Wiley
,
New York
, pp.
320
322
.
2.
Chiou
,
J. P.
, 1982, “
The Effect of Nonuniform Fluid Flow Distribution on the Thermal Performance of Solar Collector
,”
Sol. Energy
0038-092X,
29
(
6
), pp.
487
502
.
3.
Wang
,
X. A.
, and
Wu
,
L. G.
, 1990, “
Analysis and Performance of Flat-Plate Solar Collector Arrays
,”
Sol. Energy
0038-092X,
45
(
2
), pp.
71
78
.
4.
Shen
,
P. I.
, 1992, “
The Effect of Friction on Flow Distribution in Dividing and Combining Flow Manifolds
,”
ASME J. Fluids Eng.
0098-2202,
114
, pp.
121
123
.
5.
Jones
,
G. F.
, and
Lior
,
N. L.
, 1994, “
Flow Distribution in Manifolded Solar Collectors With Negligible Buoyancy Effects
,”
Sol. Energy
0038-092X,
52
(
3
), pp.
289
300
.
6.
Weitbrecht
,
V.
,
Lehmann
,
D.
, and
Richter
,
A.
, 2002, “
Flow Distribution in Solar Collectors With Laminar Flow Conditions
,”
Sol. Energy
0038-092X,
73
(
6
), pp.
433
441
.
7.
Fan
,
J.
,
Shah
,
L. J.
, and
Furbo
,
S.
, 2005, “
Flow Distribution in a Solar Collector Panel With Horizontal Fins
,”
Proceedings of the 2005 Solar World Congress
,
Orlando
.
8.
Fan
,
J.
,
Shah
,
L. J.
, and
Furbo
,
S.
, 2006, “
The Effect of Volume Flow Rate on the Efficiency of a Solar Collector
,”
EuroSun 2006
,
Glasgow, UK
.
9.
Hausner
,
R.
and
Fink
,
C.
, 2002, “
Stagnation Behavior of Solar Thermal Systems
,” IEA SHC-Task 26 Solar Combisystems Report.
10.
Vejen
,
N. K.
,
Furbo
,
S.
, and
Shah
,
L. J.
, 2004, “
Development of 12.5m2 Solar Collector Panel for Solar Heating Plants
,”
Sol. Energy Mater. Sol. Cells
0927-0248,
44
, pp.
205
223
.
11.
Furbo
,
S.
, 1997, “
Varmelagre til solvarmeanlæg
,” Institut for Bygninger og Energi, Technical University of Denmark, pp.
22
23
.
12.
Fluent Inc., 2003, Fluent Release 6.1, Lebanon, NH.
13.
Rasmussen
,
P. B.
, and
Svendsen
,
S.
, 1996, “
SolEff Program til Beregning af Solfangeres Effektivitet
,” Brugervejledning og Generel Programdokumentation, Thermal Insulation Laboratory, Technical University of Denmark.