The United States Nuclear Regulatory Commission (USNRC) has approved several extended power uprates (EPU) for Boiling Water Reactors (BWRs). In some of the BWRs, operating at the higher EPU power levels and flow rates led to high-cycle fatigue damage of Steam Dryers, including the generation of loose parts. Since those failures occurred, all BWR owners proposing EPUs have been required by the USNRC to ensure that the steam dryers would not experience high-cycle fatigue cracking. This paper provides an overview of BWR steam dryer design; the fatigue failures that occurred at the Quad Cities (QC) nuclear power plants and their root causes; a brief history of BWR EPUs; and a discussion of steam dryer modifications/replacements, alternating stress mechanisms on steam dryers, and structural integrity evaluation methods (static and alternating stress).
Overview of Boiling Water Reactor Steam Dryer Alternating Stress Assessment Procedures
Manuscript received June 9, 2017; final manuscript received September 1, 2017; published online March 5, 2018. Assoc. Editor: Jovica R. Riznic.
The United States Government retains, and by accepting the article for publication, the publisher acknowledges that the United States Government retains, a nonexclusive, paid-up, irrevocable, worldwide license to publish or reproduce the published form of this work, or allow others to do so, for United States Government purposes.
- Views Icon Views
- Share Icon Share
- Search Site
Hambric, S. A., Ziada, S., and Morante, R. J. (March 5, 2018). "Overview of Boiling Water Reactor Steam Dryer Alternating Stress Assessment Procedures." ASME. ASME J of Nuclear Rad Sci. April 2018; 4(2): 021002. https://doi.org/10.1115/1.4037898
Download citation file: