Solar power is a sustainable resource which can reduce the power generated by fossil fuels, lowering greenhouse gas emissions and increasing energy independence. The U.S. Department of Energy’s SunShot Initiative has set goals to increase the efficiency of concentrating solar power (CSP) systems. One SunShot effort to help CSP systems exceed 50% efficiency is to make use of high-temperature heat transfer fluids (HTFs) and thermal energy storage (TES) fluids that can increase the temperature of the power cycle up to 1300°C.
Sporian has successfully developed high-temperature operable pressure, temperature, thermal flux, strain, and flow sensors for gas path measurements in high-temperature turbine engines. These sensors are based on a combination of polymer derived ceramic (PDC) sensors, advanced high-temperature packaging, and integrated electronics. The overall objective is the beneficial application of these sensors to CSP systems.
Through collaboration with CSP industry stakeholders, Sporian has established a full picture of operational, interface, and usage requirements for trough, tower, and dish CSP architectures. In general, sensors should have accurate measurement, good reliability, reasonable cost, and ease of replacement or repair. Sensors in contact with hot salt HTF and TES fluids will experience temperature cycling on a daily basis, and parts of the system may be drained routinely. Some of the major challenges to high-temperature CSP implementation include molten salt corrosion and flow erosion of the sensors. Potential high-temperature sensor types that have been identified as of interest for CSP HTF/TES applications include temperature, pressure, flow, and level sensors.
Candidate solar salts include nitrate, carbonate, and chloride, with different application temperatures ranging from 550°C-900°C. Functional ceramics were soaked for 500 hours in molten nitrate, carbonate, and chloride salts, showing excellent corrosion resistance in chloride salts and good resistance in nitrate salts. The demonstration of functional ceramics in relevant HTFs laid the foundation for full prototype sensor and packaging demonstration.
Sporian has developed a packaging approach for ceramic-based sensors in various harsh gaseous environments at temperatures up to 1400°C, but several aspects of that packaging are not compatible with corrosive and electrically conductive HTFs. In addition to consulting published literature, a 300 hour soak test in molten chloride salt allowed the authors to identify suitable structural metals and ceramics.
Based on discussions with stakeholders, molten salt corrosion testing and room-temperature water flow testing, suitable for CSP sensor/packaging concepts were identified for future development, and initial prototypes have been built and tested.